IEC DETERMINATION OF TRANSFORMER AND REACTOR SOUND LEVELS. IEC Ed. Determination of transformer and reactor sound levels Defines the methods by which the sound levels of transformers, reactors and their. Find the most up-to-date version of IEC at Engineering
|Published (Last):||7 August 2005|
|PDF File Size:||13.40 Mb|
|ePub File Size:||2.25 Mb|
|Price:||Free* [*Free Regsitration Required]|
Statement of demands and needs. Lifting eyes or lugs shall be provided at suitable points of the core assembly. Motor control by signal of top oil thermometer: To assign transfer and test reports on construction sit according to fix standards. Fans The fans system including two groups Fans control: Power Transformer Power Transformer.
The fans groups shall design separate operation and independence to make iwc two fans not stop at on.
IEC | IEC Webstore
Remote control cubicle AVR: Page 7 of 19 – Equipment shall be provided supervision tap changers in times of step by step. The oil shall be a highly refined mineral oil suitable for use as an insulating and cooling medium in transformers. Commitment to client-minded and product-fit approach is a crucial value.
The remote control cubicle shall contain: Documents Flashcards Grammar checker. It shall be earthed in one point, which shall be brought out through the cover and earthed externally. Page 2 of 19 8. Over voltage, under voltage protection. IP41 The cabinet shall contain all control and protective equipment for the cooling fan system, as well as the termination of all secondary circuits.
Power quality The Power quality module allows measuring harmonics of the voltage and the current up to some hundred kHz. The Contracting Division is characterized by a light structure including committed managers capable of delivering the highest quality standard at the lowest cost.
Click to learn more. Support type Sales and product inquiry Dewesoft software support Hardware support Developer support Product feedback Other.
Thanks for contacting us. Page 1 of 19 B. The data can be represented in percentage of the fundamental frequency as required for the no-load current according to IEC standard. Outdoor Terminal and clamp out side used solid copper connected 02 open delta terminal and earthing We take all possible steps to ensure the health, safety and welfare of all employees and other persons engaged in work for the organization and any third party who comes into contact with the business.
Local cabinet control and remote control cubicle 8.
The Power transformers are located, tests, sign on conform closed electrical and check and take over by professional of manufacture. Furthermore, IEC standard requires the correction of measured power losses depending on the temperature. It shall be permitted rain water and fitted in a position easily for operating Information content: Page 13 of 19 If content of document difference of contract, manufacture must to report and notice boar to compare of difference parts.
After received request, manufacture supplies document corrected until approval by buyer. From current clamps to high-precision zero flux current transducers and Rogowsky coils. Vector group and symbol: On load tap changers: Method of neutral system: Technical Documents Before transfer equipment 10 days, manufacture supplies 08 605511 templates: The bushings shall be designed with test tap and prism a type glass with gasket. Testing of power transformers makes a couple of different measurements necessary, which are described in the international IEC standard.
The math library allows to automatically calculate parameters like the magnetizing current, the iron losses, the main inductance for ice out of the no-load test or the stray inductances out of the short-circuit tests.
The control and protection equipment of the fan- motors will be contained in a metallic weather-proof cabinet, mounted on the transformer and with provided: The Dewesoft power analyzer redefines analysis and testing process of the power transformer with its unique set of software tools and flexible hardware.
Tests report shall be including: Please download Chrome or Firefox or view our browser tips. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3. Transformer testing Testing of power transformers makes a couple of different measurements necessary, which are described in the international IEC standard. Degree of protection by enclosure: The core clamping structure shall not form closed loops and shall withstand a voltage, to the core and tank, 06551 not less than 2.